We are a family-owned, service oriented Plumbing Company.
In an effort to assist you with the answers to some of the most frequently asked questions, the Service Department at Buckeye Plumbing has provided the following answers. Please contact us if you have any particular questions we can answer for you.
If you have any questions about your plumbing, Please contact us!
Use of a simple plunger can relieve some stoppages. Failure to clear the stoppage could indicate a more severe problem and a professional should be consulted.
My showerhead and faucet aerators have a buildup of a white substance around the area where the water comes out. Is there anything I can do other than replace them?
The unsightly buildup is mineral deposits. To remove these deposits, take a plastic bag and pour a cup of vinegar in it. Place the bag over the showerhead and use a twist tie to hold it in place overnight. In the morning, remove the bag and use an old toothbrush to gently scrub off the deposits. You might be able to remove the aerators from the faucets and allow them to soak in the vinegar overnight.
When I am in the laundry room and the water heater is operating, I hear a rumbling sound coming from the water heater. What could cause this?
Rumbling sounds coming from a water heater are an indication that sediment is built up on the bottom of the water heater. What you are hearing is water that is trapped in the sediment and is boiling. This is an indication that the water heater is not operating efficiently. Sediment will not allow the heat to transfer to the water in the tank, which sends the heat up the flue. You may try draining a few gallons of water off the bottom of the water heater tank. This is done by attaching a drain hose to the valve at the bottom of the tank. Allow it to drain for about five minutes.
I am hearing a whistle sound that seems to be connected to the plumbing system. It comes and goes at times, but I can't find the cause of it. What could cause this?
The sound you are describing is usually caused by a toilet fill valve that is slowly leaking. To locate the leaking toilet, remove the lid of each toilet tank and adjust the fill valve mechanism until it stops. Once you have found the toilet causing the problem, repair or replace the fill valve.
There are four people in our house (2 adults and 2 teens). We are constantly running out of hot water. After a five-minute shower, the water starts to turn cold. This change occurred quite recently. Help!
There are two possibilities. First, the dip tube has broken off. This is a tube that forces incoming water to the bottom of the tank so that hot water will be drawn off of the top. When the dip tube breaks, cold water entering the tank mixes with the hot water and cools it down. This can occur in both gas and electric models. Second, if your water heater is electric, the lower element that heats the water may not be operating properly, thus only the upper half of the tank will heat up, The cause of this problem should be evaluated by a qualified technician.
Recently my water bills appear to be rather high. None of the faucets appear to leak. What else could contribute to a high water bill?
You may want to check to see if a toilet is leaking. First, check the water level to ensure that water is not overflowing the tank by way of the overflow pipe. This is the pipe in the middle of the tank. It has a small tubing connected to it. If water is running into the overflow, adjust the fill valve to stop the flow approximately 1 inch below the top of the overflow tube or to the water level mark stamped on the side of the tank. Second, put a few drops of food coloring into the tank to test the flush valve mechanism. If the water in the bowl changes color within 15 minutes, this is an indication that water is leaking into the toilet bowl and that the ball or flapper needs to be replaced.
Foul odors occur from a buildup of food debris within the disposer. To eliminate this odor, place ice cubes and lemon or orange peels in the disposer and let run for 30 seconds. Next, squirt a little liquid dish detergent into the disposer while it is still running. Finally, run cold water for about 30 seconds to rinse all the debris away.
I am getting a foul odor from a bathroom. We hardly ever use this bathroom except when we have company. This is embarrassing. What can we do?
Plumbing systems are designed to prevent foul odors from entering the house by means of the trap attached to fixtures. Traps contain water to seal out foul odors. If the water seal evaporates, the odors enter the house. To solve this problem, pour a bucket of water in each trap, sink, shower and floor drain. This will prevent the odors from entering the house.